• Study Resource
• Explore

Survey

* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project

Document related concepts

Mains electricity wikipedia, lookup

History of electric power transmission wikipedia, lookup

Power engineering wikipedia, lookup

Buck converter wikipedia, lookup

Switched-mode power supply wikipedia, lookup

Opto-isolator wikipedia, lookup

Alternating current wikipedia, lookup

Voltage optimisation wikipedia, lookup

Voltage regulator wikipedia, lookup

Resistive opto-isolator wikipedia, lookup

Rectifier wikipedia, lookup

Stray voltage wikipedia, lookup

Surge protector wikipedia, lookup

Distribution management system wikipedia, lookup

Current source wikipedia, lookup

Triode wikipedia, lookup

Pulse-width modulation wikipedia, lookup

Variable-frequency drive wikipedia, lookup

Ohm's law wikipedia, lookup

Islanding wikipedia, lookup

Power inverter wikipedia, lookup

Electrical ballast wikipedia, lookup

Electrical substation wikipedia, lookup

Capacitor wikipedia, lookup

Three-phase electric power wikipedia, lookup

Stepper motor wikipedia, lookup

Spark-gap transmitter wikipedia, lookup

Mercury-arc valve wikipedia, lookup

Electric power system wikipedia, lookup

Solar micro-inverter wikipedia, lookup

Power MOSFET wikipedia, lookup

Power factor wikipedia, lookup

Coilgun wikipedia, lookup

P–n diode wikipedia, lookup

Transcript
```On the other hand, if the fundamental modulation index is less than 0.6459, it can be
completely cancelled out by inserting the same amplitude of the 3rd harmonic component. For
example, M 0 =0.6459, maximum M 3 can also be 0.6459.
Figure 8.7 shows the simulation results when traditional pulsewidth modulation method is
used, and the fundamental modulation index is 0.9, which is at the higher end. The top 3
waveforms show the line-to-line voltage, measured to be at 12.7 kV. The 2nd 3 waveforms are
the capacitor currents in the top modules of each phase. Numerical simulation shows the rms
value of this ripple current that the dc link capacitor has to absorb is 47.2 A. The 3rd 3
waveforms demonstrate the phase voltage of the multilevel inverter, and the rms value is
measured to be 7.3 kV. And the 4th 3 waveforms show the 3 phase inverter output current. The
last waveform shows the dc link voltage for the top module in Phase A, which indicates the
voltage ripple peak-to-peak versus the dc link average voltage is around 2%.
Vripple( pp )
Vdc( avg )
=
34.329 V
= 2.0%
1648.2 V
(8.16)
This percentage is consistent for other modules as well.
From this simulation result, it is concluded that to maintain the dc link voltage ripple under
2% at this situation, the dc link capacitor for each H-bridge module has to be at least 3.8 mF.
Accordingly, in per unit value, this capacitance is
3.8 mF
= 18.5 p.u.
205 Âµ F
124
(8.17)
```
Related documents