Survey

* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project

Document related concepts

Induction motor wikipedia, lookup

Spark-gap transmitter wikipedia, lookup

Immunity-aware programming wikipedia, lookup

Mercury-arc valve wikipedia, lookup

Pulse-width modulation wikipedia, lookup

Stepper motor wikipedia, lookup

Power inverter wikipedia, lookup

Power engineering wikipedia, lookup

Ground loop (electricity) wikipedia, lookup

Aluminium-conductor steel-reinforced cable wikipedia, lookup

Skin effect wikipedia, lookup

Ground (electricity) wikipedia, lookup

Electrical ballast wikipedia, lookup

Single-wire earth return wikipedia, lookup

Islanding wikipedia, lookup

Multimeter wikipedia, lookup

Variable-frequency drive wikipedia, lookup

History of electric power transmission wikipedia, lookup

Triode wikipedia, lookup

Electrical substation wikipedia, lookup

Schmitt trigger wikipedia, lookup

Opto-isolator wikipedia, lookup

Resistive opto-isolator wikipedia, lookup

Earthing system wikipedia, lookup

Power MOSFET wikipedia, lookup

Power electronics wikipedia, lookup

Current source wikipedia, lookup

Switched-mode power supply wikipedia, lookup

Distribution management system wikipedia, lookup

Ohm's law wikipedia, lookup

Voltage regulator wikipedia, lookup

Surge protector wikipedia, lookup

Rectifier wikipedia, lookup

Buck converter wikipedia, lookup

Stray voltage wikipedia, lookup

Voltage optimisation wikipedia, lookup

Alternating current wikipedia, lookup

Three-phase electric power wikipedia, lookup

Mains electricity wikipedia, lookup

Transcript
```01 Electrical DeWalt
8/29/05
4:20 PM
Page 13
VOLTAGE DROP FORMULAS
The NEC® recommends a maximum 3% voltage drop for either the
branch circuit or the feeder.
Single-Phase:
2xRxIxL
VD = ____________
CM
Three-Phase:
1.732 x R x I x L
VD = ________________
CM
VD = Volts (voltage drop of the circuit)
R = 12.9 Ohms/Copper or 21.2 Ohms/Aluminum (resistance constants for a conductor that is
1 circular mil in diameter and 1 foot long at an operating temperature of 75O C.)
I = Amps (load at 100 percent)
L = Feet (length of circuit from load to power supply)
CM = Circular-Mils (conductor wire size)
2 = Single-Phase Constant
1.732 = Three-Phase Constant
CONDUCTOR LENGTH/VOLTAGE DROP
Voltage drop can be reduced by limiting the length of the conductors.
Single-Phase:
L=
CM x VD
____________
2xRxI
Three-Phase:
CM x VD
L = ________________
1.732 x R x I
CONDUCTOR SIZE/VOLTAGE DROP
Increase the size of the conductor to decrease the voltage drop of
circuit (reduce its resistance).
Single-Phase:
2xRxIxL
CM = ____________
VD
Three-Phase:
1.732 x R x I x L
CM = ________________
VD
```